Junction, Wiring Light Switch Simple Wiring Diagram Lighting Circuit 3 Switching Full Size Junction, Wiring Diagram Library Pictures
Related photos in this diagram:
Other recommended diagram ideas:
Wiring Diagram, Light Switch, Outlet Rate Pool Light Junction, Wiring Diagram Gallery - The nec now calls for an arc fault circuit interrupters (afci) breaker or afci outlet for circuits serving bedrooms. Note that if you set up an afci outlet it must be on the road facet (first one inside the circuit from the primary panel) so it is able to shield the downstream stores.
The reason of the metal junction field floor connection is to provide a safe course to ground if a hot or neutral twine were to come back loose and call the metal box, energizing the metallic container with strength and a surprise hazard. In any other case the junction field could be “warm” (or electrified) and your character will be the floor course if touched. The junction field ground ensures there’s a lower resistance course to floor than your frame!.
You’ll want to decide if the attic lighting and electric outlet are on the same circuit breaker along with what number of different lighting & retailers are that same breaker. Subsequent upload up the full load in watts for everything plugged into the other retailers then estimate the weight for what you count on to have plugged in the new attic master suite (tv, lamps, laptop, ceiling fan, portable heater, iron, blow dryer, and many others.).
Metallic junction bins and outlet bins have to be grounded. (Notice: plastic electric boxes do no longer require grounding.) I have to have hooked up the #10 green floor screw and 14 gauge floor twine while making the ground wire pigtail connections earlier, but i used to be centered on wiring the hole & switch and inadvertently ignored this important step. The correction is straightforward with wire nut pigtail connections:.
I trimmed the hot (black) and white (neutral) wires to an identical length with the naked copper ground wire, stripped about three/4 inch of insulation from the ends, then tightened the two screws on the nm cable clamp to relaxed the cable to the junction container. The nm cable clamp additionally protects the nm-b 14/2 cable from nicks by means of the pointy metals edges of the junction container knockouts.
Having proven the wiring and light transfer operation is correct, i shutoff the circuit breaker , then hooked up the uncovered work cover to the metallic junction box. The extension twine for the air handler uv treatment light is plugged into the outlet right here:.