8 Nice How To Wire A Three, Combination Switch Images
Related photos in this diagram:
Other recommended diagram ideas:
Leviton Photoelectric Switch Wiring Instructions Trusted Wiring Rh Radkan Co Leviton 3-Way Switch Diagram - The fix, of route, is to determine out which switch is installed incorrectly and flip it around so it faces the right manner. If the circuit has been properly color-coded (inside the us, that means the travelers are black and purple; it would not a lot count number that is which), you can tell this through inspection; each transfer ought to have a black cord connected to its commonplace, and a black and crimson (from the equal cable) linked to its other terminals. So if you can decide which of the 2 cables the purple belongs to, you may see which switch is hooked up incorrectly and fix it straight away.
Good enough, that works... However now we need to figure out what color the go back traveller have to be. The usa-widespread 3-wire-plus-ground cable most effective offers us the 4 colorations we have referred to: black for warm, white for impartial, purple for "alternate hot", and inexperienced for safety ground. We do not want to have to buy any other type of cable only for this uncommon utilization.
I had 2 present, one after the other stressed and powered single pole switches. One went to a light in a lobby and the opposite to the ceiling fan (the mild and fan are stressed collectively, so no longer separate switches). I disconnected and capped off the strength wire that was powering the ceiling fan/mild, and rerouted the twine to the opposite switch for the 3-way.
In case you cannot discern out which black belongs to the equal cable that the pink does, in either box, don't panic. Assuming that both switches do have a crimson and a black at their outputs, what has almost clearly befell is that the installer picked the incorrect black for at the least one of the switches. Switch the blacks at one transfer (you probably did turn off the breaker before commencing the switch box, right?!?), Turn the breaker lower back on and notice if the switches now work as supposed. If now not, turn the breaker back off and swap the blacks at the alternative switch; turn the breaker back on and try again. If it nevertheless doesn't work as anticipated, turn the breaker off one greater time, move returned to the primary transfer and positioned the blacks returned the manner they were; this is the handiest last possibility and while you switch the breaker on one ultimate time it must (eventually!) Paintings.